FIRE PREVENTION AND BUILDING SAFETY COMMISSION
Interpretation by the Fire Prevention and Building Safety Commission
Interpretation of 675 IAC 28-1-4
(NFPA 12-2005 edition), Sections 4.4.3 and 4.4.4
Purpose: The purpose of this nonrule policy document is to clarify the effect of the Indiana amendments to Sections 4.4.3 and 4.4.4, concerning testing requirements for carbon dioxide extinguishing systems.
Interpretation: The Indiana amendments require that visual and operational testing be performed, but not full discharge testing.
Posted: 07/10/2013 by Legislative Services Agency
Composed: Feb 28,2017 2:45:07AM EST
version of this document.